The first turbo-generators were water turbines which propelled electric generators. Irish engineer Charles Algernon Parsons demonstrated a DC steam-powered turbogenerator using a dynamo in 1887. and by 1901 had supplied the first large industrial AC turbogenerator of megawatt power to a plant in Eberfeld, Germany.
Turbo generators were also used on steam locomotives as a power source for coach lighting and heating systems.
Unlike hydraulic turbines which usually operate at lower speeds (100 to 600 rpm), the efficiency of a steam turbine is higher at higher speeds and therefore a turbo generator is used for steam turbines. The rotor of a turbo generator is a non-salient pole type usually with two poles.
The normal speed of a turbo generator is 1500 or 3000 rpm with four or two poles at 50 Hz (1800 or 3600 rpm with four or two poles at 60 Hz). Salient rotors will be very noisy and with a lot of windage loss. The rotating parts of a turbo generator are subjected to high mechanical stresses because of the high operation speed. To make the rotor mechanically resistant in large turbo-alternators, the rotor is normally forged from solid steel and alloys like chromium-nickel-steel or chromium-nickel-molybdenum are used. The overhang of windings at the periphery will be secured by steel retaining rings. Heavy non-magnetic metal wedges on top of the slots hold the field windings against centrifugal forces. Hard composition insulating materials, like mica and asbestos, are normally used in the slots of rotor. These material can withstand high temperatures and high crushing forces.
The stator of large turbo generators may be built of two or more parts while in smaller turbo-generators it is built up in one complete piece.
The generator is hermetically sealed to prevent escape of the hydrogen gas. The absence of oxygen in the atmosphere within significantly reduces the damage of the windings insulation by eventual corona discharges. The hydrogen gas is circulated within the rotor enclosure, and cooled by a gas-to-water heat exchanger.
Electric Turbo Compounding (ETC)
Electric Turbo Compounding (ETC) is a technology solution to the challenge of improving energy efficiency for the stationary power generation industry.
Fossil fuel based power generation is predicted to continue for decades, especially in developing economies. This is against the controversially claimed global need to reduce carbon emissions, of which, a high percentage is produced by the power sector worldwide.
ETC works by making gas and diesel-powered gensets (Electric Generators) work more effectively and cleaner, by recovering waste energy from the exhaust to improve power density and fuel efficiency.
Advantages of using ETC
Helps developing economies with unreliable or insufficient power infrastructure. 
Gives independent power providers (IPPs), power rental companies and generator OEMs (original equipment manufacturers) a competitive advantage and potential increased market share.
Improves overall efficiency of the genset, including fuel input costs and helping end-users reduce amount of fuel burned. 
Typically 4-7% less fuel consumption for both diesel and gas gensets. 
This page is based on a Wikipedia article written by authors
Text is available under the CC BY-SA 3.0 license; additional terms may apply.
Images, videos and audio are available under their respective licenses.