The Three Mile Island accident was the partial meltdown of reactor number 2 of Three Mile Island Nuclear Generating Station (TMI-2) in Dauphin County, Pennsylvania, near Harrisburg and subsequent radiation leak that occurred on March 28, 1979. It was the most significant accident in U.S. commercial nuclear power plant history. The incident was rated a five on the seven-point International Nuclear Event Scale: Accident with wider consequences.
The accident began with failures in the non-nuclear secondary system, followed by a stuck-open pilot-operated relief valve in the primary system, which allowed large amounts of nuclear reactor coolant to escape. The mechanical failures were compounded by the initial failure of plant operators to recognize the situation as a loss-of-coolant accident due to inadequate training and human factors, such as human-computer interaction design oversights relating to ambiguous control room indicators in the power plant's user interface. In particular, a hidden indicator light led to an operator manually overriding the automatic emergency cooling system of the reactor because the operator mistakenly believed that there was too much coolant water present in the reactor and causing the steam pressure release.
The accident crystallized anti-nuclear safety concerns among activists and the general public, and resulted in new regulations for the nuclear industry. It has been cited to have been a catalyst to the decline of a new reactor construction program, a slowdown that was already underway in the 1970s. The partial meltdown resulted in the release of radioactive gases and radioactive iodine into the environment.
Anti-nuclear movement activists expressed worries about regional health effects from the accident. However, epidemiological studies analyzing the rate of cancer in and around the area since the accident, determined there was a small statistically non-significant increase in the rate and thus no causal connection linking the accident with these cancers has been substantiated. Cleanup started in August 1979, and officially ended in December 1993, with a total cleanup cost of about $1 billion.
|Three Mile Island accident|
|Date||March 28, 1979|
|Time||04:00 (Eastern Time Zone UTC−5)|
|Location||Londonderry Township, Dauphin County, Pennsylvania|
|Designated||March 25, 1999|
In the night time hours preceding the incident, the TMI-2 reactor was running at 97% of power, while the companion TMI-1 reactor was shut down for refueling. The main chain of events leading to the partial core meltdown began at 4:37 am EST on March 28, 1979, in TMI-2's secondary loop, one of the three main water/steam loops in a pressurized water reactor (PWR).
The initial cause of the accident happened eleven hours earlier, during an attempt by operators to fix a blockage in one of the eight condensate polishers, the sophisticated filters cleaning the secondary loop water. These filters are designed to stop minerals and impurities in the water from accumulating in the steam generators and increasing corrosion rates in the secondary side.
Blockages are common with these resin filters and are usually fixed easily, but in this case the usual method of forcing the stuck resin out with compressed air did not succeed. The operators decided to blow the compressed air into the water and let the force of the water clear the resin. When they forced the resin out, a small amount of water forced its way past a stuck-open check valve and found its way into an instrument air line. This would eventually cause the feedwater pumps, condensate booster pumps, and condensate pumps to turn off around 4:00 am, which would in turn cause a turbine trip.
With the steam generators no longer receiving feedwater, heat and pressure increased in the reactor coolant system, causing the reactor to perform an emergency shutdown (SCRAM). Within eight seconds, control rods were inserted into the core to halt the nuclear chain reaction. The reactor continued to generate decay heat and, because steam was no longer being used by the turbine, heat was no longer being removed from the reactor's primary water loop.
Once the secondary feedwater pumps stopped, three auxiliary pumps activated automatically. However, because the valves had been closed for routine maintenance, the system was unable to pump any water. The closure of these valves was a violation of a key Nuclear Regulatory Commission (NRC) rule, according to which the reactor must be shut down if all auxiliary feed pumps are closed for maintenance. This was later singled out by NRC officials as a key failure.
The loss of heat removal from the primary loop and the failure of the auxiliary system to activate caused the primary loop pressure to increase, triggering the pilot-operated relief valve at the top of the pressurizer – a pressure active-regulator tank – to open automatically. The relief valve should have closed when the excess pressure had been released, and electric power to the solenoid of the pilot was automatically cut, but the relief valve stuck open because of a mechanical fault. The open valve permitted coolant water to escape from the primary system, and was the principal mechanical cause of the primary coolant system depressurization and partial core disintegration that followed.
Critical user interface engineering problems were revealed in the investigation of the reactor control system's user interface. Despite the valve being stuck open, a light on the control panel ostensibly indicated that the valve was closed. In fact the light did not indicate the position of the valve, only the status of the solenoid being powered or not, thus giving false evidence of a closed valve. As a result, the operators did not correctly diagnose the problem for several hours.
The design of the pilot-operated relief valve indicator light was fundamentally flawed. The bulb was simply connected in parallel with the valve solenoid, thus implying that the pilot-operated relief valve was shut when it went dark, without actually verifying the real position of the valve. When everything was operating correctly, the indication was true and the operators became habituated to rely on it. However, when things went wrong and the main relief valve stuck open, the unlighted lamp was actually misleading the operators by implying that the valve was shut. This caused the operators considerable confusion, because the pressure, temperature and coolant levels in the primary circuit, so far as they could observe them via their instruments, were not behaving as they would have if the pilot-operated relief valve were shut. This confusion contributed to the severity of the accident because the operators were unable to break out of a cycle of assumptions that conflicted with what their instruments were telling them. The problem was not correctly diagnosed until a fresh shift came in who did not have the mindset of the first shift of operators. By this time major damage had occurred.
The operators had not been trained to understand the ambiguous nature of the pilot-operated relief valve indicator and to look for alternative confirmation that the main relief valve was closed. A downstream temperature indicator, the sensor for which was located in the tail pipe between the pilot-operated relief valve and the pressurizer relief tank, could have hinted at a stuck valve had operators noticed its higher-than-normal reading. It was not, however, part of the "safety grade" suite of indicators designed to be used after an incident, and personnel had not been trained to use it. Its location on the back of the seven-foot-high instrument panel also meant that it was effectively out of sight.
As the pressure in the primary system continued to decrease, reactor coolant continued to flow, but it was boiling inside the core. First, small bubbles of steam formed and immediately collapsed, known as nucleate boiling. As the system pressure decreased further, steam pockets began to form in the reactor coolant. This departure from nucleate boiling (DNB) into the regime of "film boiling" caused steam voids in coolant channels, blocking the flow of liquid coolant and greatly increasing the fuel cladding temperature. The overall water level inside the pressurizer was rising despite the loss of coolant through the open pilot-operated relief valve, as the volume of these steam voids increased much more quickly than coolant was lost. Because of the lack of a dedicated instrument to measure the level of water in the core, operators judged the level of water in the core solely by the level in the pressurizer. Since it was high, they assumed that the core was properly covered with coolant, unaware that because of steam forming in the reactor vessel, the indicator provided misleading readings. Indications of high water levels contributed to the confusion, as operators were concerned about the primary loop "going solid," (i.e. no steam pocket buffer existing in the pressurizer) which in training they had been instructed to never allow. This confusion was a key contributor to the initial failure to recognize the accident as a loss-of-coolant accident, and led operators to turn off the emergency core cooling pumps, which had automatically started after the pilot-operated relief valve stuck and core coolant loss began, due to fears the system was being overfilled. 
With the pilot-operated relief valve still open, the pressurizer relief tank that collected the discharge from the pilot-operated relief valve overfilled, causing the containment building sump to fill and sound an alarm at 4:11 am. This alarm, along with higher than normal temperatures on the pilot-operated relief valve discharge line and unusually high containment building temperatures and pressures, were clear indications that there was an ongoing loss-of-coolant accident, but these indications were initially ignored by operators. At 4:15 am, the relief diaphragm of the pressurizer relief tank ruptured, and radioactive coolant began to leak out into the general containment building. This radioactive coolant was pumped from the containment building sump to an auxiliary building, outside the main containment, until the sump pumps were stopped at 4:39 am.
After almost 80 minutes of slow temperature rise, the primary loop's four main reactor coolant pumps began to cavitate as a steam bubble/water mixture, rather than water, passed through them. The pumps were shut down, and it was believed that natural circulation would continue the water movement. Steam in the system prevented flow through the core, and as the water stopped circulating it was converted to steam in increasing amounts. About 130 minutes after the first malfunction, the top of the reactor core was exposed and the intense heat caused a reaction to occur between the steam forming in the reactor core and the zircaloy nuclear fuel rod cladding, yielding zirconium dioxide, hydrogen, and additional heat. This reaction melted the nuclear fuel rod cladding and damaged the fuel pellets, which released radioactive isotopes to the reactor coolant, and produced hydrogen gas that is believed to have caused a small explosion in the containment building later that afternoon.
At 6 am, there was a shift change in the control room. A new arrival noticed that the temperature in the pilot-operated relief valve tail pipe and the holding tanks was excessive and used a backup valve – called a "block valve" – to shut off the coolant venting via the pilot-operated relief valve, but around 32,000 US gal (120,000 l) of coolant had already leaked from the primary loop. It was not until 165 minutes after the start of the problem that radiation alarms activated as contaminated water reached detectors; by that time, the radiation levels in the primary coolant water were around 300 times expected levels, and the general containment building was seriously contaminated.
At 6:57 am, a plant supervisor declared a site area emergency, and less than 30 minutes later station manager Gary Miller announced a general emergency, defined as having the "potential for serious radiological consequences" to the general public. Metropolitan Edison (Met Ed) notified the Pennsylvania Emergency Management Agency (PEMA), which in turn contacted state and local agencies, Governor Richard L. Thornburgh and lieutenant governor William Scranton III, to whom Thornburgh assigned responsibility for collecting and reporting on information about the accident. The uncertainty of operators at the plant was reflected in fragmentary, ambiguous, or contradictory statements made by Met Ed to government agencies and to the press, particularly about the possibility and severity of off-site radioactivity releases. Scranton held a press conference in which he was reassuring, yet confusing, about this possibility, stating that though there had been a "small release of radiation...no increase in normal radiation levels" had been detected. These were contradicted by another official, and by statements from Met Ed, who both claimed that no radioactivity had been released. In fact, readings from instruments at the plant and off-site detectors had detected radioactivity releases, albeit at levels that were unlikely to threaten public health as long as they were temporary, and providing that containment of the then highly contaminated reactor was maintained.
Angry that Met Ed had not informed them before conducting a steam venting from the plant, and convinced that the company was downplaying the severity of the accident, state officials turned to the NRC. After receiving word of the accident from Met Ed, the NRC had activated its emergency response headquarters in Bethesda, Maryland and sent staff members to Three Mile Island. NRC chairman Joseph Hendrie and commissioner Victor Gilinsky initially viewed the accident, in the words of NRC historian Samuel Walker, as a "cause for concern but not alarm". Gilinsky briefed reporters and members of Congress on the situation and informed White House staff, and at 10:00 a.m. met with two other commissioners. However, the NRC faced the same problems in obtaining accurate information as the state, and was further hampered by being organizationally ill-prepared to deal with emergencies, as it lacked a clear command structure and did not have the authority either to tell the utility what to do, or to order an evacuation of the local area.
In a 2009 article, Gilinsky wrote that it took five weeks to learn that "the reactor operators had measured fuel temperatures near the melting point". He further wrote: "We didn't learn for years – until the reactor vessel was physically opened – that by the time the plant operator called the NRC at about 8:00 a.m., roughly half of the uranium fuel had already melted."
It was still not clear to the control room staff that the primary loop water levels were low and that over half of the core was exposed. A group of workers took manual readings from the thermocouples and obtained a sample of primary loop water. Seven hours into the emergency, new water was pumped into the primary loop and the backup relief valve was opened to reduce pressure so that the loop could be filled with water. After 16 hours the primary loop pumps were turned on once again, and the core temperature began to fall. A large part of the core had melted, and the system was still dangerously radioactive.
On the third day following the accident, a hydrogen bubble was discovered in the dome of the pressure vessel, and became the focus of concern. A hydrogen explosion might not only breach the pressure vessel, but, depending on its magnitude, might compromise the integrity of the containment vessel leading to large-scale release of radioactive material. However, it was determined that there was no oxygen present in the pressure vessel, a prerequisite for hydrogen to burn or explode. Immediate steps were taken to reduce the hydrogen bubble, and by the following day it was significantly smaller. Over the next week, steam and hydrogen were removed from the reactor using a catalytic recombiner and, controversially, by venting straight to the atmosphere.
The release occurred when the cladding was damaged while the pilot-operated relief valve was still stuck open. Fission products were released into the reactor coolant. Since the pilot-operated relief valve was stuck open and the loss of coolant accident was still in progress, primary coolant with fission products and/or fuel was released, and ultimately ended up in the auxiliary building. The auxiliary building was outside the containment boundary.
This was evidenced by the radiation alarms that eventually sounded. However, since very little of the fission products released were solids at room temperature, very little radiological contamination was reported in the environment. No significant level of radiation was attributed to the TMI-2 accident outside of the TMI-2 facility. According to the Rogovin report, the vast majority of the radioisotopes released were the noble gases xenon and krypton. The report stated, "During the course of the accident, approximately 2.5 MCi (93 PBq) of radioactive noble gases and 15 Ci (560 GBq) of radioiodines were released." This resulted in an average dose of 1.4 mrem (14 μSv) to the two million people near the plant. The report compared this with the additional 80 mrem (800 μSv) per year received from living in a high altitude city such as Denver. As further comparison, a patient receives 3.2 mrem (32 μSv) from a chest X-ray—more than twice the average dose of those received near the plant. Measures of beta radiation were excluded from the report.
Within hours of the accident, the United States Environmental Protection Agency (EPA) began daily sampling of the environment at the three stations closest to the plant. Continuous monitoring at 11 stations was not established until April 1, and was expanded to 31 stations on April 3. An inter-agency analysis concluded that the accident did not raise radioactivity far enough above background levels to cause even one additional cancer death among the people in the area, but measures of beta radiation were not included. The EPA found no contamination in water, soil, sediment, or plant samples.
Researchers at nearby Dickinson College – which had radiation monitoring equipment sensitive enough to detect Chinese atmospheric atomic weapons-testing – collected soil samples from the area for the ensuing two weeks and detected no elevated levels of radioactivity, except after rainfalls (likely due to natural radon plate-out, not the accident). Also, white-tailed deer tongues harvested over 50 mi (80 km) from the reactor subsequent to the accident were found to have significantly higher levels of cesium-137 than in deer in the counties immediately surrounding the power plant. Even then, the elevated levels were still below those seen in deer in other parts of the country during the height of atmospheric weapons testing. Had there been elevated releases of radioactivity, increased levels of iodine-131 and cesium-137 would have been expected to be detected in cattle and goat's milk samples. Yet elevated levels were not found. A later study noted that the official emission figures were consistent with available dosimeter data, though others have noted the incompleteness of this data, particularly for releases early on.
According to the official figures, as compiled by the 1979 Kemeny Commission from Metropolitan Edison and NRC data, a maximum of 480 PBq (13 MCi) of radioactive noble gases (primarily xenon) were released by the event. However, these noble gases were considered relatively harmless, and only 481–629 GBq (13.0–17.0 Ci) of thyroid cancer-causing iodine-131 were released. Total releases according to these figures were a relatively small proportion of the estimated 370 EBq (10 GCi) in the reactor. It was later found that about half the core had melted, and the cladding around 90% of the fuel rods had failed, with 5 ft (1.5 m) of the core gone, and around 20 short tons (18 t) of uranium flowing to the bottom head of the pressure vessel, forming a mass of corium. The reactor vessel – the second level of containment after the cladding – maintained integrity and contained the damaged fuel with nearly all of the radioactive isotopes in the core.
Anti-nuclear political groups disputed the Kemeny Commission's findings, claiming that independent measurements provided evidence of radiation levels up to seven times higher than normal in locations hundreds of miles downwind from TMI. Arnie Gundersen, a nuclear engineer and former nuclear industry manager, said "I think the numbers on the NRC's website are off by a factor of 100 to 1,000".
Some other insiders make the same claim; Gundersen, a former nuclear industry executive who is now an expert witness in nuclear safety issues, offers evidence, based on pressure monitoring data, for a hydrogen explosion shortly before 2:00 p.m. on March 28, 1979, which would have provided the means for a high dose of radiation to occur. Gundersen cites affidavits from four reactor operators according to which the plant manager was aware of a dramatic pressure spike, after which the internal pressure dropped to outside pressure. Gundersen also notes that the control room shook and doors were blown off hinges. However official NRC reports refer merely to a "hydrogen burn." The Kemeny Commission referred to "a burn or an explosion that caused pressure to increase by 28 pounds per square inch (190 kPa) in the containment building". The Washington Post reported that "At about 2:00 pm, with pressure almost down to the point where the huge cooling pumps could be brought into play, a small hydrogen explosion jolted the reactor."
Twenty-eight hours after the accident began, William Scranton III, the lieutenant governor, appeared at a news briefing to say that Metropolitan Edison, the plant's owner, had assured the state that "everything is under control". Later that day, Scranton changed his statement, saying that the situation was "more complex than the company first led us to believe." There were conflicting statements about radioactivity releases. Schools were closed and residents were urged to stay indoors. Farmers were told to keep their animals under cover and on stored feed.
Governor Dick Thornburgh, on the advice of NRC chairman Joseph Hendrie, advised the evacuation "of pregnant women and pre-school age children...within a five-mile radius of the Three Mile Island facility." The evacuation zone was extended to a 20-mile radius on Friday, March 30. Within days, 140,000 people had left the area. More than half of the 663,500 population within the 20-mile radius remained in that area. According to a survey conducted in April 1979, 98% of the evacuees had returned to their homes within three weeks.
Post-TMI surveys have shown that less than 50% of the American public were satisfied with the way the accident was handled by Pennsylvania State officials and the NRC, and people surveyed were even less pleased with the utility (General Public Utilities) and the plant designer.
Several state and federal government agencies mounted investigations into the crisis, the most prominent of which was the President's Commission on the Accident at Three Mile Island, created by Jimmy Carter in April 1979. The commission consisted of a panel of twelve people, specifically chosen for their lack of strong pro- or anti-nuclear views, and headed by chairman John G. Kemeny, president of Dartmouth College. It was instructed to produce a final report within six months, and after public hearings, depositions, and document collection, released a completed study on October 31, 1979. The investigation strongly criticized Babcock & Wilcox, Met Ed, GPU, and the NRC for lapses in quality assurance and maintenance, inadequate operator training, lack of communication of important safety information, poor management, and complacency, but avoided drawing conclusions about the future of the nuclear industry. The heaviest criticism from the Kemeny Commission concluded that "fundamental changes were necessary in the organization, procedures, practices 'and above all—in the attitudes' of the NRC [and the nuclear industry.]" Kemeny said that the actions taken by the operators were "inappropriate" but that the workers "were operating under procedures that they were required to follow, and our review and study of those indicates that the procedures were inadequate" and that the control room "was greatly inadequate for managing an accident."
The Kemeny Commission noted that Babcock & Wilcox's pilot-operated relief valve had previously failed on 11 occasions, nine of them in the open position, allowing coolant to escape. More disturbing, however, was the fact that the initial causal sequence of events at TMI had been duplicated 18 months earlier at another Babcock & Wilcox reactor, the Davis-Besse Nuclear Power Station owned at that time by Toledo Edison. The only difference was that the operators at Davis-Besse identified the valve failure after 20 minutes, where at TMI it took 80 minutes, and the Davis-Besse facility was operating at 9% power, against TMI's 97%. Although Babcock engineers recognized the problem, the company failed to clearly notify its customers of the valve issue.
The Pennsylvania House of Representatives conducted its own investigation, which focused on the need to improve evacuation procedures.
In 1985, a television camera was used to see the interior of the damaged reactor. In 1986, core samples and samples of debris were obtained from the corium layers on the bottom of the reactor vessel and analyzed.
According to the IAEA, the Three Mile Island accident was a significant turning point in the global development of nuclear power. From 1963–1979, the number of reactors under construction globally increased every year except 1971 and 1978. However, following the event, the number of reactors under construction in the U.S. declined from 1980–1998, with increasing construction costs and delayed completion dates for some reactors. Many similar Babcock & Wilcox reactors on order were canceled; in total, 51 U.S. nuclear reactors were canceled from 1980–1984.
The 1979 TMI accident did not initiate the demise of the U.S. nuclear power industry, but it did halt its historic growth. Additionally, as a result of the earlier 1973 oil crisis and post-crisis analysis with conclusions of potential overcapacity in base load, forty planned nuclear power plants already had been canceled before the TMI accident. At the time of the TMI incident, 129 nuclear power plants had been approved, but of those, only 53 (which were not already operating) were completed. During the lengthy review process, complicated by the Chernobyl Disaster seven years later, Federal requirements to correct safety issues and design deficiencies became more stringent, local opposition became more strident, construction times were significantly lengthened and costs skyrocketed. Until 2012, no U.S. nuclear power plant had been authorized to begin construction since the year before TMI.
Globally, the end of the increase in nuclear power plant construction came with the more catastrophic Chernobyl disaster in 1986 (see graph).
Three Mile Island Unit 2 was too badly damaged and contaminated to resume operations; the reactor was gradually deactivated and permanently closed. TMI-2 had been online only 13 months but now had a ruined reactor vessel and a containment building that was unsafe to walk in. Cleanup started in August 1979 and officially ended in December 1993, with a total cleanup cost of about $1 billion. Benjamin K. Sovacool, in his 2007 preliminary assessment of major energy accidents, estimated that the TMI accident caused a total of $2.4 billion in property damages.
Initially, efforts focused on the cleanup and decontamination of the site, especially the defueling of the damaged reactor. Starting in 1985, almost 100 short tons (91 t) of radioactive fuel were removed from the site. The first major phase of the cleanup was completed in 1990, when workers finished shipping 150 short tons (140 t) of radioactive wreckage to Idaho for storage at the Department of Energy's National Engineering Laboratory. However, the contaminated cooling water that leaked into the containment building had seeped into the building's concrete, leaving the radioactive residue too impractical to remove. In 1988, the Nuclear Regulatory Commission announced that, although it was possible to further decontaminate the Unit 2 site, the remaining radioactivity had been sufficiently contained as to pose no threat to public health and safety. Accordingly, further cleanup efforts were deferred to allow for decay of the radiation levels and to take advantage of the potential economic benefits of retiring both Unit 1 and Unit 2 together.
In the aftermath of the accident, investigations focused on the amount of radioactivity released by the accident. In total approximately 2.5 megacuries (93 PBq) of radioactive gases, and approximately 15 curies (560 GBq) of iodine-131 was released into the environment. According to the American Nuclear Society, using the official radioactivity emission figures, "The average radiation dose to people living within ten miles of the plant was eight millirem (0.08 mSv), and no more than 100 millirem (1 mSv) to any single individual. Eight millirem is about equal to a chest X-ray, and 100 millirem is about a third of the average background level of radiation received by US residents in a year."
Based on these emission figures, early scientific publications, according to Mangano, on the health effects of the fallout estimated no additional cancer deaths in the 10 mi (16 km) area around TMI. Disease rates in areas further than 10 miles from the plant were never examined. Local activism in the 1980s, based on anecdotal reports of negative health effects, led to scientific studies being commissioned. A variety of epidemiology studies have concluded that the accident had no observable long term health effects.
The Radiation and Public Health Project, an organization with little credibility amongst epidemiologists, cited calculations by its member Joseph Mangano – who has authored 19 medical journal articles and a book on Low Level Radiation and Immune Disease – that reported a spike in infant mortality in the downwind communities two years after the accident. Anecdotal evidence also records effects on the region's wildlife. For example, according to one anti-nuclear activist, Harvey Wasserman, the fallout caused "a plague of death and disease among the area's wild animals and farm livestock", including a sharp fall in the reproductive rate of the region's horses and cows, reflected in statistics from Pennsylvania's Department of Agriculture, though the Department denies a link with TMI.
John Gofman used his own, non-peer reviewed low-level radiation health model to predict 333 excess cancer or leukemia deaths from the 1979 Three Mile Island accident. A peer-reviewed research article by Dr. Steven Wing found a significant increase in cancers from 1979–1985 among people who lived within ten miles of TMI; in 2009 Dr. Wing stated that radiation releases during the accident were probably "thousands of times greater" than the NRC's estimates. A retrospective study of Pennsylvania Cancer Registry found an increased incidence of thyroid cancer in counties south of TMI and in high-risk age groups but did not draw a causal link with these incidences and to the accident. The Talbott lab at the University of Pittsburgh reported finding only a few, small, mostly statistically non-significant, increased cancer risks within the TMI population, such as a non-significant excess leukemia among males being observed. The ongoing TMI epidemiological research has been accompanied by a discussion of problems in dose estimates due to a lack of accurate data, as well as illness classifications.
The TMI accident enhanced the credibility of anti-nuclear groups, who had predicted an accident, and triggered protests around the world. (President Carter—who had specialized in nuclear power while in the United States Navy—told his cabinet after visiting the plant that the accident was minor, but reportedly declined to do so in public in order to avoid offending left-wing Democrats who opposed nuclear power.)
Members of the American public, concerned about the release of radioactive gas from the accident, staged numerous anti-nuclear demonstrations across the country in the following months. The largest demonstration was held in New York City in September 1979 and involved 200,000 people, with speeches given by Jane Fonda and Ralph Nader. The New York rally was held in conjunction with a series of nightly "No Nukes" concerts given at Madison Square Garden from September 19–23 by Musicians United for Safe Energy. In the previous May, an estimated 65,000 people – including California Governor Jerry Brown – attended a march and rally against nuclear power in Washington, D.C.
In 1981, citizens' groups succeeded in a class action suit against TMI, winning $25 million in an out-of-court settlement. Part of this money was used to found the TMI Public Health Fund. In 1983, a federal grand jury indicted Metropolitan Edison on criminal charges for the falsification of safety test results prior to the accident. Under a plea-bargaining agreement, Met Ed pleaded guilty to one count of falsifying records and no contest to six other charges, four of which were dropped, and agreed to pay a $45,000 fine and set up a $1 million account to help with emergency planning in the area surrounding the plant.
According to Eric Epstein, chair of Three Mile Island Alert, the TMI plant operator and its insurers paid at least $82 million in publicly documented compensation to residents for "loss of business revenue, evacuation expenses and health claims". Also according to Harvey Wasserman, hundreds of out-of-court settlements have been reached with alleged victims of the fallout, with a total of $15 million paid out to parents of children born with birth defects. However, a class action lawsuit alleging that the accident caused detrimental health effects was rejected by Harrisburg U.S. District Court Judge Sylvia Rambo. The appeal of the decision to U.S. Third Circuit Court of Appeals also failed.
The Three Mile Island accident inspired Charles Perrow's Normal Accident Theory, in which an accident occurs, resulting from an unanticipated interaction of multiple failures in a complex system. TMI was an example of this type of accident because it was "unexpected, incomprehensible, uncontrollable and unavoidable."
Perrow concluded that the failure at Three Mile Island was a consequence of the system's immense complexity. Such modern high-risk systems, he realized, were prone to failures however well they were managed. It was inevitable that they would eventually suffer what he termed a 'normal accident'. Therefore, he suggested, we might do better to contemplate a radical redesign, or if that was not possible, to abandon such technology entirely.
"Normal" accidents, or system accidents, are so-called by Perrow because such accidents are inevitable in extremely complex systems. Given the characteristic of the system involved, multiple failures which interact with each other will occur, despite efforts to avoid them. Events which appear trivial initially cascade and multiply unpredictably, creating a much larger catastrophic event.
Normal Accidents contributed key concepts to a set of intellectual developments in the 1980s that revolutionized the conception of safety and risk. It made the case for examining technological failures as the product of highly interacting systems, and highlighted organizational and management factors as the main causes of failures. Technological disasters could no longer be ascribed to isolated equipment malfunction, operator error or acts of God.
Following the Three Mile Island (TMI) power plant's partial core melt on March 28, 1979, President Jimmy Carter commissioned a study, Report of the President's Commission on the Accident at Three Mile Island (1979). Subsequently, Admiral Hyman G. Rickover was asked to testify before Congress in the general context of answering the question as to why naval nuclear propulsion (as used in submarines) had succeeded in achieving a record of zero reactor-accidents (as defined by the uncontrolled release of fission products to the environment resulting from damage to a reactor core) as opposed to the dramatic one that had just taken place at Three Mile Island. In his testimony, he said:
Over the years, many people have asked me how I run the Naval Reactors Program, so that they might find some benefit for their own work. I am always chagrined at the tendency of people to expect that I have a simple, easy gimmick that makes my program function. Any successful program functions as an integrated whole of many factors. Trying to select one aspect as the key one will not work. Each element depends on all the others.
On March 16, 1979, twelve days before the accident, the movie The China Syndrome premiered, and was initially met with backlash from the nuclear power industry, claiming it to be "sheer fiction" and a "character assassination of an entire industry."
In the film, television reporter Kimberly Wells (Jane Fonda) and her cameraman Richard Adams (Michael Douglas) secretly film a major accident at a nuclear power plant while taping a series on nuclear power. The operating crew notices a high-pressure measurement on a gauge and begin to reduce coolant flow to lower the pressure. This does not appear to work, and they continue reducing the flow until an emergency indicator lamp warns of extremely low pressure. Confused by the conflicting indications, an operator taps the gauge, at which point the needle becomes unstuck and swings over to indicate extremely low pressure. The reactor is SCRAMed. In the aftermath, the plant supervisor, Jack Godell (Jack Lemmon) discovers potentially catastrophic safety violations at the plant and with Wells' assistance attempts to raise public awareness of these violations. At one point in the film, an official tells Jane Fonda's character that an explosion at the plant "could render an area the size of the state of Pennsylvania permanently uninhabitable." 
After the release of the film, Fonda began lobbying against nuclear power. In an attempt to counter her efforts, the then elderly Edward Teller, a nuclear physicist and long-time government science adviser best known for contributing to the Teller-Ulam design breakthrough that made hydrogen bombs possible, personally lobbied in favor of nuclear power. Teller suffered a heart attack shortly after the incident and joked that he was the only person whose health was affected.
Currently, Unit 1 — which was not involved in the 1979 accident — is owned and operated by Exelon Nuclear, a subsidiary of Exelon. Unit 1 was sold to AmerGen Energy Corporation, a joint venture between Philadelphia Electric Company (PECO), and British Energy, in 1998. In 2000, PECO merged with Unicom Corporation to form Exelon Corporation, which acquired British Energy's share of AmerGen in 2003. In 2009, Exelon Nuclear absorbed AmerGen and dissolved the company. Exelon Nuclear operates TMI Unit 1, Clinton Power Station and several other nuclear facilities. 
Unit 1 had its license temporarily suspended following the incident at Unit 2. Although the citizens of the three counties surrounding the site voted by an overwhelming margin to retire Unit 1 permanently in a non-binding resolution in 1982, it was permitted to resume operations in 1985 following a 4-1 vote by the Nuclear Regulatory Commission. General Public Utilities Corporation, the plant's owner, formed General Public Utilities Nuclear Corporation (GPUN) as a new subsidiary to own and operate the company's nuclear facilities, including Three Mile Island. The plant had previously been operated by Metropolitan Edison Company (Met-Ed), one of GPU's regional utility operating companies. In 1996, General Public Utilities shortened its name to GPU Inc and in 1998, it sold Unit 1 to AmerGen.
General Public Utilities was legally obliged to continue to maintain and monitor the site, and therefore retained ownership of Unit 2 when Unit 1 was sold to AmerGen in 1998. GPU Inc. was acquired by FirstEnergy Corporation in 2001, and subsequently dissolved. FirstEnergy then contracted out the maintenance and administration of Unit 2 to AmerGen. Unit 2 has been administered by Exelon Nuclear since 2003, when Exelon Nuclear's parent company, Exelon, bought out the remaining shares of AmerGen, inheriting FirstEnergy's maintenance contract. Unit 2 continues to be licensed and regulated by the Nuclear Regulatory Commission in a condition known as Post Defueling Monitored Storage (PDMS).
The TMI-2 reactor has been permanently shut down with the reactor coolant system drained, the radioactive water decontaminated and evaporated, radioactive waste shipped off-site, reactor fuel and core debris shipped off-site to a Department of Energy facility, and the remainder of the site being monitored. The owner planned to keep the facility in long-term, monitoring storage until the operating license for the TMI-1 plant expired, at which time both plants would be decommissioned. In 2009, the NRC granted a license extension which allowed the TMI-1 reactor to operate until April 19, 2034. In 2017 it was announced that operations would cease by 2019 due to financial pressure from cheap natural gas.
|April 1974||Reactor-1 online|
|February 1978||Reactor-2 online|
|March 1979||TMI-2 accident occurred. Containment coolant released into environment.|
|April 1979||Containment steam vented to the atmosphere in order to stabilize the core.|
|July 1980||Approximately 1,591 TBq (43,000 curies) of krypton were vented from the reactor building.|
|July 1980||The first manned entry into the reactor building took place.|
|November 1980||An Advisory Panel for the Decontamination of TMI-2, composed of citizens, scientists, and State and local officials, held its first meeting in Harrisburg, Pennsylvania.|
|December 1980||U.S. 96th Congressional session passes U.S. legislation establishing a five-year nuclear safety, research, demonstration, and development program.|
|July 1984||The reactor vessel head (top) was removed.|
|October 1985||Defueling began.|
|July 1986||The off-site shipment of reactor core debris began.|
|August 1988||GPU submitted a request for a proposal to amend the TMI-2 license to a "possession-only" license and to allow the facility to enter long-term monitoring storage.|
|January 1990||Defueling was completed.|
|July 1990||GPU submitted its funding plan for placing $229 million in escrow for radiological decommissioning of the plant.|
|January 1991||The evaporation of accident-generated water began.|
|April 1991||NRC published a notice of opportunity for a hearing on GPU's request for a license amendment.|
|February 1992||NRC issued a safety evaluation report and granted the license amendment.|
|August 1993||The processing of accident-generated water was completed involving 2.23 million gallons.|
|September 1993||NRC issued a possession-only license.|
|September 1993||The Advisory Panel for Decontamination of TMI-2 held its last meeting.|
|December 1993||Post-Defueling Monitoring Storage began.|
|October 2009||TMI-1 license extended from April 2014 until 2034.|
(In 1979 Foreword:) "...we arrive at 333 fatal cancers or leukemias."
Thyroid cancer incidence has not increased in Dauphin County, the county in which TMI is located. York County demonstrated a trend toward increasing thyroid cancer incidence beginning in 1995, approximately 15 years after the TMI accident. Lancaster County showed a significant increase in thyroid cancer incidence beginning in 1990. These findings, however, do not provide a causal link to the TMI accident.
The NRC conducted detailed studies of the accident's radiological consequences, as did the Environmental Protection Agency, the Department of Health, Education and Welfare (now Health and Human Services), the Department of Energy, and the Commonwealth of Pennsylvania. Several independent groups also conducted studies. The approximately 2 million people around TMI-2 during the accident are estimated to have received an average radiation dose of only about 1 millirem above the usual background dose. To put this into context, exposure from a chest X-ray is about 6 millirem and the area's natural radioactive background dose is about 100-125 millirem per year for the area. The accident's maximum dose to a person at the site boundary would have been less than 100 millirem above background. In the months following the accident, although questions were raised about possible adverse effects from radiation on human, animal, and plant life in the TMI area, none could be directly correlated to the accident. Thousands of environmental samples of air, water, milk, vegetation, soil, and foodstuffs were collected by various government agencies monitoring the area. Very low levels of radionuclides could be attributed to releases from the accident. Comprehensive investigations and assessments by several well respected organizations, such as Columbia University and the University of Pittsburgh, have concluded that in spite of serious damage to the reactor, the actual release had negligible effects on the physical health of individuals or the environment.
Apparently the valves were closed for routine maintenance, in violation of one of the most stringent rules that the Nuclear Regulatory Commission has. The rule states simply that auxiliary feed pumps can never all be down for maintenance while the reactor is running.
|url=missing title (help).
Arnie Gundersen — a nuclear engineer and former nuclear industry executive turned whistle-blower — has done his own analysis, which he shared for the first time at a symposium in Harrisburg last week. "I think the numbers on the NRC's website are off by a factor of 100 to 1,000," he said.
These findings, however, do not provide a causal link to the TMI accident
Island]—The Kemeny Report on the Accident at Three Mile Island.Edwin E. Kintner
Edwin E. Kintner (1920–2010) was an American nuclear pioneer and engineer and a U.S. Navy captain who was in charge of de-contamination of the Three Mile Island accident.Gloria Borger
Gloria Anne Borger (born September 22, 1952) is an American political pundit, journalist, and columnist. Borger was previously a contributing editor and columnist for U.S. News & World Report magazine and is now chief political analyst at CNN. She was formerly the national political correspondent for CBS News. Since joining CNN in 2007, she has appeared on a variety of their shows, including The Situation Room.Borger previously worked as the co-anchor of CNBC’s Capital Report, appeared on CBS's Face the Nation and 60 Minutes II. Borger covered the Three Mile Island accident for Newsweek in 1979.Human error
Human error has been cited as a primary cause contributing factor in disasters and accidents in industries as diverse as nuclear power (e.g., the Three Mile Island accident), aviation (see pilot error), space exploration (e.g., the Space Shuttle Challenger Disaster and Space Shuttle Columbia disaster), and medicine (see medical error). Prevention of human error is generally seen as a major contributor to reliability and safety of (complex) systems.
Human error is one of the many contributing causes of risk events.List of anti–nuclear power groups
Anti-nuclear power groups have emerged in every country that has had a nuclear power programme. Protest movements against nuclear power first emerged in the USA, at the local level, and spread quickly to Europe and the rest of the world. National nuclear campaigns emerged in the late 1970s. Fuelled by the Three Mile Island accident and the Chernobyl disaster, the anti-nuclear power movement mobilised political and economic forces which for some years "made nuclear energy untenable in many countries".Some of these anti-nuclear power organisations are reported to have developed considerable expertise on nuclear power and energy issues. In 1992, the chairman of the Nuclear Regulatory Commission said that "his agency had been pushed in the right direction on safety issues because of the pleas and protests of nuclear watchdog groups".Metropolitan Edison Co. v. People Against Nuclear Energy
Metropolitan Edison Co. v. People Against Nuclear Energy, 460 U.S. 766 (1983), was a case decided by the United States Supreme Court.Musicians United for Safe Energy
Musicians United for Safe Energy, or MUSE, is an activist group founded in 1979 by Jackson Browne, Graham Nash, Bonnie Raitt, Harvey Wasserman and John Hall. The group advocates against the use of nuclear energy, forming shortly after the Three Mile Island nuclear accident in March 1979. MUSE organized a series of five No Nukes concerts held at Madison Square Garden in New York in September 1979. On September 23, 1979, almost 200,000 people attended a large rally staged by MUSE on the then-empty north end of the Battery Park City landfill in New York.Other musicians performing at the concerts included Crosby, Stills, and Nash, Bruce Springsteen and the E Street Band, James Taylor, Carly Simon, Chaka Khan, the Doobie Brothers, Jesse Colin Young, Gil Scott-Heron, Tom Petty, Dan Fogelberg, Poco and others. The album No Nukes, and a film, also titled No Nukes, were both released in 1980 to document the performances. A full No Nukes concert featuring Browne and Crosby, Stills & Nash was also filmed near the beach in Ventura, California, at the Ventura County Fairgrounds, but none of that footage made it into the final cut.
In the 2006 midterm elections, Hall was elected to the United States House of Representatives from New York's 19th congressional district, on a platform that included intensive investment in alternative energy. He defeated the incumbent, Sue Kelly.
In 2007, Raitt, Nash, and Browne, as part of the No Nukes group, recorded a music video of the Buffalo Springfield song "For What It's Worth".Thirty two years after the No Nukes concert in New York, on August 7, 2011, a MUSE benefit concert was held at Shoreline Amphitheater in Mountain View, CA. to raise money for MUSE and for Japanese tsunami/nuclear disaster relief. Artists included Jackson Browne, Bonnie Raitt, John Hall, Graham Nash, David Crosby, Stephen Stills, Kitaro, Jason Mraz, Sweet Honey in the Rock, the Doobie Brothers, Tom Morello, and Jonathan Wilson. The show was powered off-grid.No Nukes (film)
No Nukes is a 1980 documentary and concert film that contained selections from the September 1979 Madison Square Garden concerts by the Musicians United for Safe Energy collective, with Jackson Browne, Graham Nash, Bonnie Raitt, and John Hall being the key organizers of the event and guiding forces behind the film. Also included were scenes of the organizers getting the event together, expounding upon the dangers of nuclear power, and staging an anti-nuclear rally at Battery Park in New York City.Normal Accidents
Normal Accidents: Living with High-Risk Technologies is a 1984 book by Yale sociologist Charles Perrow, which provides a detailed analysis of complex systems from a sociological perspective. It was the first to "propose a framework for characterizing complex technological systems such as air traffic, marine traffic, chemical plants, dams, and especially nuclear power plants according to their riskiness". Perrow argues that multiple and unexpected failures are built into society's complex and tightly coupled systems. Such accidents are unavoidable and cannot be designed around.Perrow's argument, based on systemic features and human error, is that big accidents tend to escalate, and technology is not the problem, the organizations are. Each of these principles is still relevant today.Nuclear reactor accidents in the United States
The United States Government Accountability Office reported more than 150 incidents from 2001 to 2006 of nuclear plants not performing within acceptable safety guidelines. According to a 2010 survey of energy accidents, there have been at least 56 accidents at nuclear reactors in the United States (defined as incidents that either resulted in the loss of human life or more than US$50,000 of property damage). The most serious of these was the Three Mile Island accident in 1979. Davis-Besse Nuclear Power Plant has been the source of two of the top five most dangerous nuclear incidents in the United States since 1979. Relatively few accidents have involved fatalities.Robert Del Tredici
Robert Del Tredici is a Canadian photographer, artist and teacher, who documented the impact of the 1979 Three Mile Island accident on the community. His first book of photographs and interviews, The People of Three Mile Island (Sierra Club Books, 1980), was a social critique of nuclear power. His second book, At Work in the Fields of the Bomb (Harper & Row, 1987), discussed the US nuclear weapons industry and won the 1987 Olive Branch Book Award for its contribution to world peace.He founded the Atomic Photographers Guild in 1987 along with photographers Carole Gallagher and Harris Fogel.
Del Tredici has a bachelor’s degree in philosophy, and a master’s in comparative literature. He currently teaches photography and the history of animated film in Concordia University in Montreal.Shoreham Nuclear Power Plant
The Shoreham Nuclear Power Plant was a completed General Electric nuclear boiling water reactor located adjacent to Long Island Sound in East Shoreham, New York.
The plant was built between 1973 and 1984 by the Long Island Lighting Company (LILCO). The plant faced considerable public opposition after the 1979 Three Mile Island accident and the 1986 Chernobyl disaster. There were large protests and two dozen local groups opposed the plant.
In 1983, Suffolk County determined that the county could not be safely evacuated in the event of a serious nuclear accident at the plant. Governor Mario Cuomo ordered state officials not to approve any LILCO-sponsored evacuation plan—effectively preventing the plant from operating at full capacity. The plant was completed in 1984 and in 1985 LILCO received federal permission for low-power (5 percent power) tests.
By 1989, it became apparent that not enough local communities would sign on to the evacuation plan for the plant ever to be able to open. On May 19, 1989, LILCO agreed not to operate the plant in a deal with the state under which most of the $6 billion cost of the unused plant was passed on to Long Island residents. In 1992, the Long Island Power Authority bought the plant from LILCO. The plant was fully decommissioned in 1994.The China Syndrome
The China Syndrome is a 1979 American disaster thriller film directed by James Bridges and written by Bridges, Mike Gray, and T. S. Cook. It tells the story of a television reporter and her cameraman who discover safety coverups at a nuclear power plant. It stars Jane Fonda, Jack Lemmon, and Michael Douglas, with Douglas also serving as the film's producer. The cast also features Scott Brady, James Hampton, Peter Donat, Richard Herd, and Wilford Brimley.
"China syndrome" is a fanciful term—not intended to be taken literally—that describes a fictional result of a nuclear meltdown, where reactor components melt through their containment structures and into the underlying earth, "all the way to China."
The China Syndrome premiered at the 1979 Cannes Film Festival, where it competed for the Palme d'Or while Lemmon received the Best Actor prize. The film was released theatrically on March 16, 1979, twelve days before the Three Mile Island nuclear accident in Dauphin County, Pennsylvania, which gave the film's subject matter an unexpected prescience. Upon release the film was a critical and commercial success with critics praising the film's screenplay, direction and thriller elements and Fonda's and Lemmon's performances. The film grossed $51.7 million on a production budget of $5.9 million. It received four nominations at the 52nd Academy Awards: Best Actor (Lemmon), Best Actress (Fonda), Best Art Direction (George Jenkins, Arthur Jeph Parker), and Best Original Screenplay.Three Mile Island (disambiguation)
Three Mile Island is the Three Mile Island Nuclear Generating Station in eastern Pennsylvania.
Three Mile Island also may refer to:
Matters related to the Three Mile Island plant:
Three Mile Island accident, a partial core meltdown occurring in 1979
Three Mile Island accident health effects
Three Mile Island: Thirty Minutes to Meltdown (1982)
Three Mile Island: A Nuclear Crisis in Historical Perspective (2004)
Three Mile Island (video game), a 1979 simulation game for the Apple II
Three Mile Island (Lake Winnipesaukee), an island in New Hampshire, United StatesThree Mile Island Nuclear Generating Station
Three Mile Island Nuclear Generating Station (TMI) is a nuclear power plant located on Three Mile Island in Londonderry Township, Pennsylvania, on the Susquehanna River just south of Harrisburg. It has two separate units, TMI-1 (owned by Exelon Generation) and TMI-2 (owned by FirstEnergy Corp). The plant is widely known for having been the site of the most significant accident in United States commercial nuclear energy, on March 28, 1979, when TMI-2 suffered a partial meltdown. As per the Nuclear Regulatory Commission (NRC) report, the accident resulted in no deaths or injuries to plant workers or members of nearby communities. Follow-up epidemiology studies have linked no incidents of cancer to the accident.
The reactor core of TMI-2 has since been removed from the site, but the site has not been decommissioned. In July 1998, Amergen Energy (now Exelon Generation) agreed to purchase TMI-1 from General Public Utilities for $100 million.Three Mile Island is so named because it is located three miles downriver from Middletown, Pennsylvania. The plant was originally built by General Public Utilities Corporation, later renamed GPU Incorporated. The plant was operated by Metropolitan Edison Company (Met-Ed), a subsidiary of the GPU Energy division. During 2001 GPU Inc. merged with FirstEnergy Corporation.The NRC defines two emergency planning zones around nuclear power plants: a plume exposure pathway zone with a radius of 10 miles (16 km), concerned primarily with exposure to, and inhalation of, airborne radioactive contamination, and an ingestion pathway zone of about 50 miles (80 km), concerned primarily with ingestion of food and liquid contaminated by radioactivity.The 2010 U.S. population within 10 miles (16 km) of Three Mile Island was 211,261, an increase of 10.9 percent in a decade, according to an analysis of U.S. Census data for msnbc.com. The 2010 U.S. population within 50 miles (80 km) was 2,803,322, an increase of 10.3 percent since 2000. Cities within 50 miles include Harrisburg (12 miles to city center), York (13 miles to city center), and Lancaster (24 miles to city center).Exelon has been operating Unit 1 at Three Mile Island at a loss since 2015. On May 30, 2017, the company said it would consider ceasing operations at Unit 1 in 2019 due to high costs of operating the plant unless there was government action. On May 8, 2019, Exelon announced that the remaining reactor still operating will be shut down by September 30.Unit 2, which has been dormant since the accident in 1979, is still owned by FirstEnergy, and it is estimated to close in 2036.Three Mile Island accident health effects
The health effects of the 1979 Three Mile Island nuclear accident are widely, but not universally, agreed to be very low. The American Nuclear Society concluded here that average local radiation exposure was equivalent to a chest X-ray, and maximum local exposure equivalent to less than a year's background radiation. The U.S. BEIR report on the Biological Effects of Ionizing Radiation states that "[t]he collective dose equivalent resulting from the radioactivity released in the Three Mile Island accident was so low that the estimated number of excess cancer cases to be expected, if any were to occur, would be negligible and undetectable." A variety of epidemiology studies have concluded that the accident has had no observable long term health effects. One dissenting study is "A reevaluation of cancer incidence near the Three Mile Island nuclear plant" by Dr. Steven Wing of the University of North Carolina. In this study, Dr. Wing and his colleagues argue that earlier findings had "logical and methodological problems" and conclude that "cancer incidence, specifically lung cancer and leukemia, increased following the TMI accident in areas estimated to have been in the pathway of radioactive plumes than in other areas."
Other dissenting opinions can be found in the Radiation and Public Health Project, whose leader, Joseph Mangano, has questioned the safety of nuclear power since 1985.Wendall Woodbury
Wendall J. Woodbury (June 20, 1942 – October 20, 2010) was an American television journalist and news anchor. He spent much of his career as a reporter for WGAL-TV in Lancaster, Pennsylvania, from 1968 until his retirement from broadcast news in 1992 as a feature reporter. He was known for a series of segments called "Wendall's World" while at WGAL. Woodbury was the first television anchor in the United States to report on the Three Mile Island accident as the story broke in 1979.