IEC 60870 part 6 is one of the IEC 60870 set of standards which define systems used for telecontrol (supervisory control and data acquisition) in electrical engineering and power system automation applications. The IEC Technical Committee 57 (Working Group 03) have developed part 6 to provide a communication profile for sending basic telecontrol messages between two systems which is compatible with ISO standards and ITU-T recommendations.
These standards include:
A typical national power grid includes a hierarchy of control centres to manage the generation, transmission, and distribution of power throughout the grid:
Prior to the development of electronics and telecommunications networks all co-ordination between control centres was carried out by telephone. However, the development of SCADA (supervisory control and data acquisition) systems allowed remote control and monitoring of electrical plant from centralised control centres.
Initially individual SCADA manufacturers developed their own proprietary "closed" protocols for communicating from a control centre to electrical equipment in the field. These were followed by the development of "open" industry-standard protocols such as DNP3 and IEC 61850. However, none of these communication protocols were suited to the requirements of communicating between control centres. To meet these special requirements for communication and co-ordination between control centres the IEC developed the IEC 60870 set of standards.
The Inter-Control Center Communications Protocol (ICCP or IEC 60870-6/TASE.2) is being specified by utility organizations throughout the world to provide data exchange over wide area networks (WANs) between utility control centers, utilities, power pools, regional control centers, and Non-Utility Generators. ICCP is also an international standard: International Electrotechnical Commission (IEC) Telecontrol Application Service Element 2 (TASE.2).
Inter-utility real time data exchange has become critical to the operation of interconnected systems in most parts of the world. For example, the development of electricity markets has seen the management of electricity networks by a functional hierarchy that is split across boundaries of commercial entities. At the top level there is typically a system operator with coordination responsibilities for dispatch and overall system security. Below this are regional transmission companies that tie together distribution companies and generating companies. In continental power systems there is now considerable interconnection across international borders. ICCP allows the exchange of real time and historical power system information including status and control data, measured values, scheduling data, energy accounting data and operator messages.
Historically there has been reliance on custom or proprietary links and protocols to exchange real time data between systems. ICCP began as an effort to develop an international standard for real-time data exchange within the electric power utility industry. A working group was formed in 1991 to develop a protocol standard, develop a prototype to test the specification, submit the specification to the IEC for standardisation and carry out interoperability testing between developing vendors. The initial driver was to meet European Common Market requirements in 1992. The official designation of the first protocol was TASE.1 (Telecontrol Application Service Element-1). The second protocol TASE.2  making use of the Manufacturing Message Specification (MMS) appears to be the version that has become the most popular.
In the US, ICCP networks are widely used to tie together groups of utility companies, typically a regional system operator with transmission utilities, distribution utilities and generators. Regional operators may also be connected together to co-ordinate import and export of power between regions across major inter-ties.
Basic ICCP functionality is specified as “Conformance Blocks” listed below. The objects that are used to convey the data are defined in various parts of IEC 60870-6.
Block Description Data Examples:
ICCP is based on client / server principles. Data transfers result from a request from a control centre (client) to another control centre (server). Control centres may be both clients and servers. ICCP operates at the application layer in the OSI model. As such any physical interfaces, transport and network services that fit this model are supported. TCP/IP over Ethernet (802.3) seems to be the most common. ICCP may operate over a single point-to-point link between two control centres; however, the more general case is for many control centres and a routed wide area network. The logical connections or “associations” between control centres are completely general. A client may establish associations with more than one server and a client may establish more than one association with the same server. Multiple associations with same server can be established at different levels of quality of service so that high priority real time data is not delayed by lower priority or non real time data transfers.
ICCP does not provide authentication or encryption. These services are normally provided by lower protocol layers. ICCP uses “Bilateral Tables” to control access. A Bilateral Table represents the agreement between two control centres connected with an ICCP link. The agreement identifies data elements and objects that can be accessed via the link and the level of access permitted. Once an ICCP link is established, the contents of the Bilateral Tables in the server and client provide complete control over what is accessible to each party. There must be matching entries in the server and client tables to provide access to data and objects.
The wide acceptance of ICCP by the utility industry has resulted in several ICCP products being on the market. Although interoperability is not regarded as a high risk area, the standard is such that an implementation does not have to support all conformance blocks in order to claim compliance with the standard. A minimal implementation only requires Block 1. Only those blocks necessary to achieve the required functionality need be implemented. It is also not necessary to support all objects defined in the standard for any particular block. Extensive interoperability testing between products of some of the major vendors has been a feature of ICCP protocol development. Independent reports are available, as no doubt are reports from vendors. An ICCP purchaser must define functionality required in terms of conformance blocks required and the objects within those blocks. Application profiles for the ICCP client and server conformances must match if the link is to operate successfully.
ICCP is a real time data exchange protocol providing features for data transfer, monitoring and control. For a complete ICCP link there need to be facilities to manage and configure the link and monitor its performance. The ICCP standard does not specify any interface or requirements for these features that are necessary but nevertheless do not affect interoperability. Similarly failover and redundancy schemes and the way the SCADA responds to ICCP requests is not a protocol issue so is not specified. These non protocol specific features are referred to in the standard as “local implementation issues”. ICCP implementers are free to handle these issues any way they wish. Local implementation is the means that developers have to differentiate their product in the market with added value. Additional money spent on a product with well-developed maintenance and diagnostic tools may well be saved many times over during the life of the product if use of the ICCP connection is expected to grow and change.
Commercial ICCP products are generally available for one of three configurations:
As an embedded protocol the ICCP management tools and interfaces are all part of the complete suite of tools for the SCADA. This configuration offers maximum performance because of the direct access to the SCADA database without requiring any intervening buffering. This approach may not be available as an addition to a legacy system. The ICCP application may be restricted to accessing only the SCADA environment in which it is embedded.
A networked server making use of industry standard communications networking to the SCADA host may provide performance approaching that of an embedded ICCP application. On the application interface side the ICCP is not restricted to the SCADA environment but is open to other systems such as a separate data historian or other databases. Security may be easier to manage with the ICCP server segregated from the operational real time systems. The gateway processor approach is similar to the networked server except it is intended for legacy systems with minimal communications networking capability and so has the lowest performance. In the most minimal situation the ICCP gateway may communicate with the SCADA host via a serial port in a similar manner to the SCADA RTUs.
DNP3 (Distributed Network Protocol) is a set of communications protocols used between components in process automation systems. Its main use is in utilities such as electric and water companies. Usage in other industries is not common. It was developed for communications between various types of data acquisition and control equipment. It plays a crucial role in SCADA systems, where it is used by SCADA Master Stations (a.k.a. Control Centers), Remote Terminal Units (RTUs), and Intelligent Electronic Devices (IEDs). It is primarily used for communications between a master station and RTUs or IEDs. ICCP, the Inter-Control Center Communications Protocol (a part of IEC 60870-6), is used for inter-master station communications. Competing standards include the older Modbus protocol and the newer IEC 61850 protocol.ICCP
ICCP may refer to:
IBS Center for Climate Physics, the first Earth Science research center within the Institute for Basic Science (IBS), South Korea
Impressed Current Cathodic Protection, a system used to control the corrosion using anodes connected to a DC power source
Ingeniería de Caminos Canales y Puertos, a professional engineering discipline also known as Civil engineering
Institute for Certification of Computing Professionals, a non-profit organization that develops and administers certifications for the information technology industry
Inter-Chassis Control Protocol, is a networking protocol used by MC-LAG to control communication between two chassis.
Inter-Control Center Communications Protocol, an operational protocol used by electrical utilities as part of IEC 60870-6
International Climate Change Partnership, an industry group dealing with climate change issues
International Committee for Coal and Organic Petrology, a professional organization of more than 200 scientists representing more than 35 countries, engaged in many different branches, fundamental and applied, of coal and organic petrology.
Islamic Community Center of Phoenix, a mosque in Phoenix, Arizona.
Issue Competition Comparative Project, a comparative international social science research project about party competition.IEC 60870
In electrical engineering and power system automation, the International Electrotechnical Commission 60870 standards define systems used for telecontrol (supervisory control and data acquisition). Such systems are used for controlling electric power transmission grids and other geographically widespread control systems. By use of standardized protocols, equipment from many different suppliers can be made to interoperate. IEC standard 60870 has six parts, defining general information related to the standard, operating conditions, electrical interfaces, performance requirements, and data transmission protocols. The 60870 standards are developed by IEC Technical Committee 57 (Working Group 03).IEC 62351
IEC 62351 is a standard developed by WG15 of IEC TC57. This is developed for handling the security of TC 57 series of protocols including IEC 60870-5 series, IEC 60870-6 series, IEC 61850 series, IEC 61970 series & IEC 61968 series. The different security objectives include authentication of data transfer through digital signatures, ensuring only authenticated access, prevention of eavesdropping, prevention of playback and spoofing, and intrusion detection.Remote terminal unit
A remote terminal unit (RTU) is a microprocessor-controlled electronic device that interfaces objects in the physical world to a distributed control system or SCADA (supervisory control and data acquisition) system by transmitting telemetry data to a master system, and by using messages from the master supervisory system to control connected objects. Other terms that may be used for RTU are remote telemetry unit and remote telecontrol unit.
|Industrial control system|
|Automatic meter reading|
|Automobile / Vehicle|